Cambridge Housing Authority Meets LEED Certification Using Aerosealadmin
Excessive duct leakage was preventing LEED certification for the Cambridge Housing Authority (CHA). To be LEED certified, the ductwork used to ventilate 40 bathrooms in the newly constructed five-story building had to demonstrate a total leakage rate below 250 CFM. With the first test results from hand sealing the air ducts with mastic showing 900+ CFM, CHA was not even close to LEED status. The CHA had a big problem. There were thousands of dollars in federal rebate dollars that the CHA could not receive until it achieved LEED certification.
The mechanical contractor sent in a team of hand-sealers to find and fix the leaks using traditional hand sealing methods (mastic, tape). After several costly attempts at manually sealing the ductwork, leakage rates remained too high to meet LEED requirements. That’s when the CHA decided to try Aeroseal, a computer-controlled approach to sealing air ducts. Aeroseal emits a precise amount of aerosolized sealant into pressurized ductwork. As a result, the ductwork is sealed from the inside to simultaneously find and seal the leaks more consistently than manual sealing.
- Building: Cambridge Housing Authority LEED Construction
- Location: Cambridge, Massachusetts
- General Contractor: P.J. Dionne
- Aeroseal Contractors: Aspen Air Duct Cleaning
- Goal: Meet required duct leakage rate of 250 CFM or less in order to achieve LEED certification
- Before Aeroseal: Average 900+ CFM of leakage
- After Aeroseal: Average 40 CFM of leakage
- Results: Met LEED certification requirements; Reduced leakage by approximately 95%
Cambridge Housing Authority, Cambridge, MA Duct Sealing Project
The entire Aeroseal duct sealing process took only two workdays to complete (much faster than hand sealing) and was conducted while other construction work continued throughout the building. In only a weekend, Aspen Air Duct Cleaning set up its Aeroseal equipment, prepared the ductwork for sealing, and finished the entire building.
The mechanical contractors confirmed what the computer-controlled Aeroseal duct sealing technology reported upon completion of the process – sealing the ductwork with Aeroseal brought leakage down to 47 CFM – well below the LEED certification requirements. The CHA was so pleased with the results that it continued discussions with Aspen Air Duct Cleaning regarding the possibility of future Aeroseal duct sealing projects.
“I’m a 100% believer in Aeroseal. I wish we had had it specified for the job in the beginning.” Don Stock, Project Manager, P.J. Dionne
“Initially, there was a lot of skepticism among the building engineers that aeroseal would do the trick – especially when they learned that the sealant doesn’t coat the entire inside of the ductwork but instead, accumulates around the individual leaks. After seeing the results, they are all now believers and big fans of the technology.” Bob Corsetti, Aspen Duct Cleaning
We Can Help You Too.
To learn more about using Aeroseal to meet duct sealing requirements for LEED certification and improving the heating/cooling comfort, indoor air quality (IAQ), and energy efficiency of your home or building, email us a message to firstname.lastname@example.org or give us a call 937-428-9300.