ESCO Estimates $3500/yr Energy Savings with AerosealJonathan at Aeroseal
When McKinstry gives their customers a quote on either the cost or the amount of energy savings they can expect from one of their building performance projects, they guarantee the results. It’s therefore critical that they are confident in their estimations before the work begins.
That guarantee, along with the experience they’ve gained over five decades of contracting work, helped McKinstry land a renovation project with Northern Washington’s Skagit County, where local officials wanted to install 70 new HVAC systems into their government administration building. After opening its doors in 1977, officials thought it was time to add air conditioning to the 3-story 35,000 sq. ft building.
- Building: Skagit County Courthouse Administration Blg.
- Location: Mt. Vernon, Washington
- Contractor: McKinstry
- Duct Sealing Contractors: Aeroseal LLC
- Goals: Upgrade HVAC system. Lower energy costs
- Before Aeroseal: 15,414 CFM of leakage
- After Aeroseal: 1,600 CFM of leakage
- Results: 90% reduction of leakage. Estimated energy cost savings of approximately $3,500 each year.
Photo: Skagit County Courthouse,
Mt. Vernon, Washington
McKinstry knew that if they could salvage the building’s existing duct system, they would eliminate much of the expense and disruption that comes from replacing existing ductwork. Testing of the current duct system, however, showed excessive leakage – something they would have to remedy if they were to qualify for the state’s results-based energy savings rebate program.
Familiar with aeroseal duct sealing technology, McKinstry proposed that the existing duct system be
aerosealed tight and then reused for the newly installed AC systems. By sealing from the inside of the ducts,
the aeroseal technology would allow the contractors to quickly find and seal the leaks without demolition.
The computerized process would generate the before-and-after report needed to secure the rebate.
Using their proprietary energy savings model, the Aeroseal experts were able to closely estimate the amount of energy savings that would come from aerosealing. Armed with this information, McKinstry was able to guarantee huge energy savings and a renovation project that could be accomplished with minimal disruption.
It took the Aeroseal team just 4 days to seal the building’s four primary duct systems serving all 70 new units. Aeroseal reduced duct leakage by 90%, delivering a 4-year ROI based on energy cost savings.
“Using their energy model, Aeroseal was able to give us an estimate on the energy cost savings we could expect from sealing the ductwork. Given the large amount generated by their modeling, we decided to play it safe and guarantee a more conservative number. In the end, the savings turned out to be even more than Aeroseal’s original estimate – and it allowed us to deliver on an impressive 4-year ROI.”
“With such a unique approach to duct sealing, there was a bit of apprehension before the Aeroseal team arrived. But after the first sealing event went flawlessly, we had no further worries whatsoever. The sealing technology worked wonders. I would recommend it for use in older retrofit projects and even in new buildings where building performance matters.”