VA Hospital Meets Codes with Aeroseal Duct SealingJonathan at Aeroseal
Just months after opening the doors to its new Veterans House, the VA medical center of Indianapolis, Indiana discovered that the building’s Energy Recovery Ventilation (ERV) system wasn’t working properly. The diagnosis: intake and exhaust ductwork running throughout the building and through the ERV were full of leaks, making it impossible to balance and adjust airflow. Strict government standards require a leakage rate of 10% or less. Pretesting showed a leakage rate that exceeded 45% in some areas. Faced with this reality, VA administrators were contemplating a massive setback – the prospect of having to empty out the facility, close its doors and begin tearing down walls and ceilings in order to access the ductwork and manually seal the leaks. Lucky for all involved, the project’s construction company did a little Internet research and came across an alternative solution…Aeroseal.
- Property Owners: Veterans Administration
- Engineers: RL Turner Corporation; Indiana
- Aeroseal Experts: Reupert Heating & Air
- Type: 3-story temporary housing facility
- Goal: Meet ERV specifications
- Before Aeroseal: 900+ CFM* of total leakage
- After Aeroseal: 63 CFM of total leakage
- Results: Reduced average leakage by 93%
Veterans House, Indianapolis Indiana Aeroseal Duct Sealing Project.
It took Reupert Heating & Air just three days to aeroseal the building’s entire ductwork – the alternative option would have taken a year or more to complete and hundreds of thousands of dollars more in added demolition and construction costs to accomplish. Aeroseal works from the inside of the duct system to locate and seal leaks, so finding and sealing all of the various holes and gaps throughout the entire duct system could be accomplished without disturbing any of the newly finished construction. The aeroseal technology is safe and highly effective. The work was done over Memorial Day weekend and the building was open for veterans and their families the following day.
Aeroseal was first brought in to seal the exhaust ducts that ran from the bathroom grilles to the ERV. After VA administrators saw how effective and unobtrusive the sealing process was, the scope of the sealing project was expanded to include all four airflow systems.
“Aeroseal proved to be the right solution for the problem. I’ve been in this business for quite a long time and I’ve seen quicky solutions come and go, but this one actually held water…or I should say ‘air’ as the case may be.”
Roudebush VA Medical Center
“I did my research and found that short of tearing down and starting over, there was only one option – Aeroseal. For retrofits and new construction projects like this, it is the ideal solution. The technology prevented a much more expensive and invasive procedure.”
RL Turner Corporation
“The before and after reports showed us the results. The VA’s independent contractors then came in and confirmed what we already knew – Aeroseal did the job. And while we were simply looking to reduce leakage and fulfill specification requirements, it doesn’t take a rocket scientist to add up the difference Aeroseal made in system performance and know that it also provided a significant savings for somebody’s checkbook.”
Reupert Heating & Air
About Aeroseal Technology
- Developed at Lawrence Berkeley National Laboratory in 1994.
- Research for aeroseal technology was partially funded by the U.S. Department of Energy.
- Aeroseal is the only duct sealant technology that is applied from the inside of the duct system. It is delivered as a non-toxic aerosol mist that seeks out and plugs leaks.
- Aeroseal has proven to be 95% effective at sealing air duct leaks.